The M100 Stopswitch is a simple inductive shaft speed monitoring device. The self-contained unit has a single set point, which signals when the shaft has stopped rotating. It can be used for process control, motion detection and stopped shaft indication. An inductive sensing device located in the nose of the M100 enclosure will detect a metal target. This target can be an existing bolt head or device attached to a shaft. The M100 Stopswitch requires no calibration and provides an output when the shaft has stopped rotating.
- Stopped Motion Monitor
- Inductive Proximity Sensor
- Single Trip Set Point
- Totally Sealed Construction (Submersible)
- Non-Contacting and Fail-Safe
Part Numbers & Accessories:
- M1001V10A - Stopswitch M100
- M1001V10AG - Stopswitch M100 (gas approved)
- WG1-8A-BR - Whirligig (target/bracket/guard)
- MAG2000M - Mag-Con Magnetic Connector for Whirligig
M100 Stopswitch – Detects Dangerous Stop Conditions
The X400 Elite is a microprocessor controlled low cost alarm indicator panel for use with level indicators, hazard controls and limit switch sensors. The X400 accepts signals from different sources in up to 8 zones, and is able to cause alarm and shutdown of the machine when an alarm condition has been detected. Alarm and status LEDs on the lid of the X400 provide quick location of alarm conditions. Alarm muting can be performed at the panel or by an optional remote push button to silence external alarms. If the system is muted, it will automatically reactivate when a new alarm is triggered. Testing can also be activated at the panel, providing full system verification.
In the product documentation, there is a reference to "load". What is it and how big does it have to be?
Load is not a resistor, it is referring to any item that pulls current (PLC input, ice cube relay, etc.) and draws less than 200 mA.
When checking the 2 wire M300 with a voltage meter, it is always showing full voltage no matter if the shaft is turning or not. Why is the sensor not changing states?
The sensor will not function correctly until a load is connected to it, maximum current through the sensor is 200 mA..